Verification on Delay Time Adequacy of RSG GAS (Reaktor Serba Guna - G.A. Siwabessy) Control Elements
Available Online October 2014.
- https://doi.org/10.2991/icp-14.2014.22How to use a DOI?
- Delay time; control element; dropping time; instrumentation response.
- The capability of control elements to manage the reactor operation does not merely relay on their negative reactivity worth, but also the speed required to shutdown the reactor when operation state leads to an accident condition. The response speed of control elements is characterized by delay time which comprises of instrumentation response and dropping time. The adequacy verification on delay time was performed against fast reactivity transient due to inadvertant control rod withdrawal by observing safety parameters at peak power. Three delay times were analized using PARET/ANL code for fast reactivity transients. The calculation results confirmed that the delay time may not exceed 0.5 s.
- Open Access
- This is an open access article distributed under the CC BY-NC license.
Cite this article
TY - CONF AU - Azizul Khakim PY - 2014/10 DA - 2014/10 TI - Verification on Delay Time Adequacy of RSG GAS (Reaktor Serba Guna - G.A. Siwabessy) Control Elements PB - Atlantis Press SP - 109 EP - 113 SN - 2352-541X UR - https://doi.org/10.2991/icp-14.2014.22 DO - https://doi.org/10.2991/icp-14.2014.22 ID - Khakim2014/10 ER -