The Harm of Harmonic in Power Distribution Network and Its Equipment
- https://doi.org/10.2991/isrme-15.2015.422How to use a DOI?
- harmonic; electric energy loss; distribution network; equipment
Through several examples, describes the harmonic distribution network and its equipment hazards. Harmonics can cause distribution transformers demonstration power loss and additional loss increases, resulting in reduced aging transformer oil and insulation properties, triggering a distribution transformer discharge breakdown or burn accidents; harmonics is amplified in a capacitor bank, and cause the capacitor bank fuse group burst, tripping and other accidents; harmonics cause the motor to reverse, vibration, noise and temperature; harmonic electromagnetic voltage transformer prone to occur ferromagnetic resonance over-voltage; harmonics resulting in increased distribution network line losses. Awareness and understanding harmonics, harmonic provide for effective governance scientific theory.
- © 2015, the Authors. Published by Atlantis Press.
- Open Access
- This is an open access article distributed under the CC BY-NC license (http://creativecommons.org/licenses/by-nc/4.0/).
Cite this article
TY - CONF AU - Yanjun Pang AU - Peng Liu AU - Xue Wang AU - Rui Tong AU - Xinhua Zhao AU - Yingying Yang AU - Hongzhi Jiao AU - Huiyan Cao AU - Mei Xu AU - Lei Wang AU - Wenlong Zhu PY - 2015/04 DA - 2015/04 TI - The Harm of Harmonic in Power Distribution Network and Its Equipment BT - Proceedings of the 2015 International Conference on Intelligent Systems Research and Mechatronics Engineering PB - Atlantis Press SP - 2039 EP - 2043 SN - 1951-6851 UR - https://doi.org/10.2991/isrme-15.2015.422 DO - https://doi.org/10.2991/isrme-15.2015.422 ID - Pang2015/04 ER -