Procedure for Calculating Building Chilled and Hot Water Differential Pressure Setpoint
- 10.2991/lemcs-15.2015.105How to use a DOI?
- Pump speed control; Flow-rate; Differential pressure setpoint; VFD; Recommissioning
The calculation of the building differential pressure (DP) setpoint based on the water flow-rate is discussed in this paper. How to find the coefficient (k) of water piping system in any case is the key in the calculation. The condition of the building DP calculation is documented to make sure its correction. The theory of pump working point matching water system curve is applied to find k in the procedure. After adjusting the pressure drop on each air handling unit and water balance for the system, the measurement of the water flow-rate and the building DP can be taken and system k can be calculated. Then, an example of the building DP calculation is given.
- © 2015, the Authors. Published by Atlantis Press.
- Open Access
- This is an open access article distributed under the CC BY-NC license (http://creativecommons.org/licenses/by-nc/4.0/).
Cite this article
TY - CONF AU - Rijin Sun AU - Chenggang Liu AU - Rundong Liu PY - 2015/07 DA - 2015/07 TI - Procedure for Calculating Building Chilled and Hot Water Differential Pressure Setpoint BT - Proceedings of the International Conference on Logistics, Engineering, Management and Computer Science PB - Atlantis Press SP - 551 EP - 554 SN - 1951-6851 UR - https://doi.org/10.2991/lemcs-15.2015.105 DO - 10.2991/lemcs-15.2015.105 ID - Sun2015/07 ER -