Analysis and Prevention of Tubeburst in Rear Platen Superheater of Boiler
Ke Liu, Hui Liu, Fanjun Hou
Available Online June 2016.
- https://doi.org/10.2991/mecs-17.2017.28How to use a DOI?
- Boiler; Water blocking; Rear platen superheate
- Tube burst occurred on Rear Platen Superheater in No.4 boiler of a power plant. Failed to timely discharge condensate water after an emergency shutdown boiler, and then start again, which leading to water blocking in superheater unit caused tube burst. Contrasting the water blocking accidents recent years in this boiler, corresponding preventive measures are formulated, which have certain reference value to theproblems of tubeburst caused by water blocking of the same type boiler.
- Open Access
- This is an open access article distributed under the CC BY-NC license.
Cite this article
TY - CONF AU - Ke Liu AU - Hui Liu AU - Fanjun Hou PY - 2016/06 DA - 2016/06 TI - Analysis and Prevention of Tubeburst in Rear Platen Superheater of Boiler BT - Proceedings of the 2017 2nd International Conference on Machinery, Electronics and Control Simulation (MECS 2017) PB - Atlantis Press SN - 2352-5401 UR - https://doi.org/10.2991/mecs-17.2017.28 DO - https://doi.org/10.2991/mecs-17.2017.28 ID - Liu2016/06 ER -