Ground Source Heat Pump with Passive Heat Compensation Tower
Yanli Song, Tao Du, Dong Ren
Available Online April 2017.
- https://doi.org/10.2991/iceesd-17.2017.124How to use a DOI?
- Ground source heat pump , Heat loss , The Passive Heat Compensation Tower
- The collation and analysis of the existing problems of ground source heat pump system and the existing solutions, based on the research and development of a new patch of ground source heat pump tower, through the experiment, obtained in the air temperature is 27.1 , the wet bulb temperature is 19.8 , the dew point temperature of 15.5 , relative humidity is 46%, supplement run a tower in the ground source heat pump water temperature rise after passive, 2.43 , after the water temperature gradually declines, in ninth after the operation, the temperature rise of 0.15 , tenth times after the operation, the temperature rise of 0.1 , up to the tower using passive soil heat is feasible.
- Open Access
- This is an open access article distributed under the CC BY-NC license.
Cite this article
TY - CONF AU - Yanli Song AU - Tao Du AU - Dong Ren PY - 2017/04 DA - 2017/04 TI - Ground Source Heat Pump with Passive Heat Compensation Tower BT - 2017 6th International Conference on Energy, Environment and Sustainable Development (ICEESD 2017) PB - Atlantis Press SN - 2352-5401 UR - https://doi.org/10.2991/iceesd-17.2017.124 DO - https://doi.org/10.2991/iceesd-17.2017.124 ID - Song2017/04 ER -